This Duct leak test video will show how ducts are tested, Testing your duct system will let you know if there are any leaks in your heating or air conditioning duct system. We pressurize your ducts with a special blower that measures the amount of air input and a probe placed into a register lets us know the amount of air leaking from your duct system.
These leaks can be coming from your ducts not being sealed properly or cavities in your home being used as ducts to transfer the air.
Places to check for duct leaks are:
Holes in ducting. If you turn your fan or A/C on and go into your attic you could feel around the ducting for leaks. Also check around the plenums.
Flex Duct and the metal boot to the register should have zip ties on both layers of the duct if using flex duct.
Register should be removed and chalked between the metal boot and the drywall.
Air can leak back into the attic through this gap. If the gap is large enough it can draw insulation and dirt from your attic and blow it into your home.
The plenum is the metal box at each end of your furnace or air handler. This is where your ducts are attached. It is very important this is sealed also. Check where the ducts are attached to the start collar. Again there needs to be zip ties on the flex duct. Also check around all 4 sides and corners of the plenum. In some cases a sheet metal screw should be used to secure any loose openings.
Ceiling return grill should be checked. The ceiling return grill should be remove to see if it was sealed. If not you should seal the metal box to the drywall like you did with the registers. This is very important. The return will draw the dirt and insulation from your attic into the duct system and block the coil if you have refrigerated air, and blow the rest in your home. Sensitive people will find it harder to breath or a heavy chest.
Platform return grill. If your furnace is located in a closet it is most likely leaking from below the platform. If you look under the platform through the return grill and see the 2x4s exposed on the wall sides there is a good chance those 2x4s go all the way to your attic. If there are no fire blocks in the wall it will draw air from your attic into the furnace. This area should be sealed to stop air from infiltrating from the attic. Most A/C companies use "duct board" and mastic to seal this area under the platform.